It is designed for mounting in JA-19xPL multi-purpose boxes or on a DIN rail. The outputs are isolated from the bus. It is set using the DIP switch.
It is not addressable (does not occupy a position in the security system).
|Power supply||via the control panel bus 12 V (9 ... 15 V)|
|Current consumption during backup open/closed outputs||5 mA/10m A|
|Current consumption for cable selection||10 mA|
|Maximum current from an output +U (electronic fuse)||<100 mA (all connected devices must be added for current calculations)|
|Dimensions||77 x 40 x 15 mm|
|Classification||level 2 in acc. with EN 50131-1, only when module is located in a JA-194PL or JA-195PL box
using the JA-111H TRB module
|Environment according to||EN 50131-1 II. general indoor|
|Operation temperature range||-10 °C to +40 °C|
|It also meets the requirements of||EN 50131-3, EN 50130-4 ed. 2+A1, EN 55032, EN 50581|