The JA-83K control panel is a modular unit, with 50 addresses (marked 01 to 50). The heart of the unit is the JA-83K main board with 10 wired inputs (up to 30 using JA-82C module(s)).
Wireless peripherals can be used when the control panel is equipped with a JA-82R module.
The control panel can accommodate a backup battery of up to 18 Ah. Three sections are available when using partial arming or a split system. The control panel provides signals for sirens (internal and external) and 2 programmable outputs. Up to 50 codes and proximity cards can be set up.
The following additional modules can be plugged into this board:
A communicator can also be used with the control panel:
The JA-68 outputs module can also be used with the control panel – e.g. to provide a link to the transmitter for communication with the surveillance centre.
|External power source||230 V / 50 Hz, max 0.1 A, CLASS PROTECTION II|
|Power supply||type A (EN 50131-6)|
|Backup-battery||12 V, 7 to 18 Ah, typical battery lifetime approx. 5 years|
|Maximum recharge time||72 hours|
|Backup power output (+U terminal)||maximum continuous load 1.1 A (when an 18 Ah backup battery is used)|
|Backup power output (+L terminal)||maximum continuous load 0.2 A|
power outputs +U +L have electronic fuse
|Number of wireless device addresses||50 (requires a JA-82R module)|
|Communications frequency (JA-82R)||868 MHz ISM band|
|Number of hard-wired inputs||10 (up to 30 if two JA-82C are plugged in), double balanced inputs, with triggering and tamper functions (each wireless detector blocks the hard-wired input to which it is assigned)|
|External warning output EW*||switching to GND, max. 0.5A|
|Internal warning output IW*||switching to GND, max. 0.5A|
|Programmable outputs*||PGX, PGY max. 0.1 A, switching to GND|
|Event memory||255 latest events, including date and time stamping|
|Intruder alarm signal or message||after 1 or 2 events (adjustable)|
|Tamper signal or message||after 1 event|
|Wrong authorisation code alarm signal or message||after 10 events|
|Fault signal or message||after 1 event|
|Security grade||2 according to EN 50131-1, EN 50131-6, and EN 50131-5-3|
|Environmental||class II. indoor-general (-10 to +40°C) compliant with EN 50131-1|
|Radio emissions||ETSI EN 300220|
|EMC||EN 50130-4, EN 55022|
|Can be operated according to ERC REC 70-03|
|* these signals are also transmitted wirelessly to wireless sirens and AC and UC receiver modules.|